b. Remove associated hardware from cable entrance plates and remove plates with attached electrical
c. Remove associated hardware holding switchboard to channel mounting base.
d. Install removable lifting eyes on top of emergency generator switchboard, if removed.
e. Attach lifting fixture to lifting eyes.
Repair is by replacement of emergency generator switchboard.
The following procedure describes actions required to complete
installation of emergency generator switchboard once the
switchboard has been placed into position in vessel.
a. Remove lifting fixture from lifting eyes.
b. Install associated hardware to secure switchboard to channel mounting base.
c. Install cable entrance plates with attached electrical cables with associated hardware.
d. Connect all electrical wiring to buses and terminal boards. Remove tags.
e. Install all removed component parts as specified in paragraphs 2-291 through 2-297,2-301 and 2-304 .
f. Turn on power to emergency generator switchboard and remove tags.
g. Set circuit breakers, switches, and rheostats to their required positions and observe meters and