MAINTENANCE OF PIPING SYSTEM, FOAM PROPORTIONERS
3-262. REPLACE/REPAIR WELDED FITTINGS.
This task covers:
Tool kit, general mechanic's,
At Ship Service Switchboard, set FIRE
PUMP 1 and FIRE PUMP 2 circuit
Torch outfit, cutting and
breakers to the OFF position. Tag
welding medium duty, oxygen
switch "Out of Service-Do Not
and acetylene, 3433-00-357-8116
Tool kit, welder, 5180-00-754-0661
General Safety Instructions
Piping system, foam proportioners
P/N 8529048, refer to
Ensure system is tagged to prevent
Warning tags, Item 1, Appendix C
operation during maintenance.
Utility pail, Item 13, Appendix C
Generated pressure could cause
Use extreme care when breaking
system connections. Escaping
pressure and/or fluids could
Clean up spills immediately. Spills
create an unsafe working area.
Exercise extreme caution when
working with flammables.
Refer to paragraph 3-217 for procedures.